Soudal | Fire Rated Expanding Foam
Soudafoam FR is a Fire Rated Expanding Foam Filler from Soudal which has a Fire Rating of up to 240 minutes - BS476(20) 4 Hour Fire Rating Warrington depending on configuration. Soudafoam FR may be used for the Fire Retardant installation of window and door frames, for fire and smoke retardant sealing of connections between partition walls, ceilings and floors, plus much more.
Supplied in a 750ml Cans, available in Gun Grade application only.
Soudafoam FR is a Fire Rated, rapid curing, one component polyurethane expanding foam filler which has a fire rating of up to 240 minutes - BS476(20) 4 Hour Fire Rating Warrington depending on configuration.
Soudafoam FR Fire rated expanding foam has excellent thermal and acoustic properties, it expands up to 35-40 times its initial volume and has excellent primerless adhesion on most construction materials.
Fire Retardant up to 240 minutes.
Efficient seal against smoke and gas.
Excellent adhesion on most substrates (exempt Teflon, PE and PP).
High thermal and acoustical insulation.
High bonding strength.
Very good filling characteristics.
Excellent stability: no shrink or post expansion.
Can be painted after full cure.
Fire Retardant installation of window and door frames.
Fire and smoke retardant sealing of connections between partition walls, ceilings and floors.
Filling of cavities.
Fire Retardant sealing of all openings in roof constructions.
Fire Retardant sealing of cable- and pipe penetrations.
Fire Retardant creation of a sound-proof screen.
Fire Retardant bonding of insulation materials.
Fire Retardant application of sound-deadening layers.
Improving thermal insulation in cold store areas.
Product Basis: Polyurethane Foam Filler
Box Yield FEICA TM1003 (750ml Cannister): 43 Litres
Joint Yield FEICA TM1002 (750ml Cannister): 24 Metres
Acoustic Rating ISO 717-1: 62 dB
Application Temperatures: +5°C to +40°C
Test Report 9297 - University of Ghent Standard NBN 713.020
Test Report 13492B - Warrington Fire Ghent: Classification report according to EN 13501-2
BS476 : Part 20 - Warrington Fire Research Report
ETA - 13/0280
Shake the aerosol can for at least 20 seconds. Attach the can onto the Applicator Gun. Surface should be free from grease and dust.
Moisten surfaces with a water sprayer prior to application.
For non-conventional substrates a preliminary adhesion test is recommended.
Fill holes and cavities approximately ¾ full as the foam will expand.
Repeat shaking regularly during application.
If you have to work in layers repeat moistening after each layer. Fresh foam can be removed using Soudal Gun & Foam Cleaner or acetone.
Cured foam can only be removed mechanically or with Cured PU Foam Remover. Never burn away cured foam.
Important: Soudafoam FR may not extrude from the can the same way as standard PU Expanding Foams, this is due to the make up of the product, being much more 'viscous' in nature due to the added Fire Retardant additives. This however has no bearing on the overall expansion rate of the product when curing.
Take the usual labour hygiene into account.
Always wear gloves and goggles during application. See our Safety & PPE Products.
Consult label and material safety data sheet for more information.
We've added to your cart